# ÖKOfen calculation Flow temp See setpoint

Heating, insulation, ventilation, VMC, cooling ... short thermal comfort. Insulation, wood energy, heat pumps but also electricity, gas or oil, VMC ... Help in choosing and implementation, problem solving, optimization, tips and tricks ...
jmproneau
I discovered econologic
posts: 2
Registration: 05/11/22, 11:01
x 1

## ÖKOfen calculation Flow temp See setpoint

Hello,

On Pellematic compact 18KW with pellematic touch (Insulated 1900 house, Eure, 11 radiators, 200m2)
In the water law adjustment phase (no ambient influence)
I never manage to find by calculation the figure of the T° Setpoint departure Cf . Thus: in a well-stabilized regime:
Water law: 31,5 and 1,1
Outdoor temp 13,9
Comfort temp 20,6 (auto mode), measured 20,3
Flow setpoint temp Cf: 33,9 (measured 33,7)
When I do the intuitive (dumb?) calculation: Starting setpoint T° = 31,5 + 1,1*(20,6-13,9)=38,9.
I always find about 5° above the boiler flow setpoint temperature.
Does anyone have any light on this subject?
I attach a graph file.
Graph_20230104.png (130.22 KiB) Accessed 734 times

Jean-Marie
1 x
LioDuBDL
I discovered econologic
posts: 1
Registration: 15/01/23, 16:44

## Re: ÖKOfen calculation Flow temp See setpoint

Hello,

I have a Pellematic compact 14KW with pellematic touch.
After a few hours of research and calculations, I found a formula that so far in my case works pretty well:

Flow Setpoint Temp = - Slope *(T Ext-13,5)+Foot-1,5 + ((Int Temp Setpoint-18,5)*(1+Slope)) + (Int Probe Factor*(Int Temp- Setpoint Int Temp))

Lionel
0 x
jmproneau
I discovered econologic
posts: 2
Registration: 05/11/22, 11:01
x 1

## Re: ÖKOfen calculation Flow temp See setpoint

Whew! It can't be invented!..... Congratulations for this work.!
it looks like a classical principle modified empirically...
I will make a small excel table to follow according to my water law (32°, 1,1)
Thanks again!!
Jean-Marie
0 x

• Similar topics
Replies
views
Last message

• 80 Replies
2666 views
Last message by Christophe View the latest post
13/03/23, 12:19

### A subject posted in the forum : Heating, insulation, ventilation, VMC, cooling ...

• 15 Replies
912 views
Last message by Pilpoill View the latest post
11/02/23, 07:05

### A subject posted in the forum : Heating, insulation, ventilation, VMC, cooling ...

• 5 Replies
823 views
Last message by Flytox View the latest post
27/01/23, 19:39

### A subject posted in the forum : Heating, insulation, ventilation, VMC, cooling ...

• 3 Replies
484 views
Last message by Christophe View the latest post
20/01/23, 13:41

### A subject posted in the forum : Heating, insulation, ventilation, VMC, cooling ...

• 2 Replies
806 views
Last message by MARTIN5335 View the latest post
10/01/23, 21:05

### A subject posted in the forum : Heating, insulation, ventilation, VMC, cooling ...

Back to "Heating, insulation, ventilation, VMC, cooling ..."

#### Who is online ?

Users browsing this forum : No registered users and 163 guests